dixell. DEFAULT SETTING VALUES. تا تا تست ه تا تن تا نا م ع. XR60C signals and records temperature alarms, together with their duration and max. View and Download Emerson Dixell XR60C installing and operating instructions online. Digital controller with defrost and fans management. Dixell XR60C. Dixell Srl reserves the right to change the composition of its products, even without or faulty operation send the instrument back to the distributor or to Dixell Srl.
|Published (Last):||7 November 2008|
|PDF File Size:||5.31 Mb|
|ePub File Size:||20.28 Mb|
|Price:||Free* [*Free Regsitration Required]|
EMERSON DIXELL XR60C INSTALLING AND OPERATING INSTRUCTIONS Pdf Download.
Other parameters are used to control the. In case of failure or faulty operation send the instrument back to the distributor or to “Dixell. This function managed by the Fct parameter is designed to avoid short cycles of fans, that.
This is used to make sure circulation of air only. Universal variable speed ac drive for induction and permanent magnetmotors pages. To display target set point; in programming mode it selects a parameter or confirm an. In case of applications in rixell environments, the use of mains filters our mod. Flexible machine integration through communications 50 pages.
This manual also for: Do not expose to water or moisture: On the display the following message is shown: This manual is part of the product and should be kept near the instrument for easy and quick. Page of 4 Go. Don’t show me this message again.
Don’t have an account? Ensure that the wires for probes, loads and the power supply are separated and far enough. Then the instrument displays the temperature once again. To confirm the operation, the “rSt” message starts blinking and the normal x6r0c.
They have three relay outputs to control compressor, fan, and defrost, which can be.
Emerson Dixell XR60C Installing And Operating Instructions
The instrument must not be opened. By pressing ‘print’ button you will dixlel only current page. To see the last temperature alarm happened; in programming mode it browses the. Comments to this Manuals Your Name.
Unidrive hs series; unidrive m series. XR60C signals and records temperature alarms, together with their duration and max value. Hold the SET key pressed for more than 3s, while the recorded alarm is displayed. Check the supply voltage is correct before connecting the instrument. Digital controller with defrost and fans management. After defrost, there is a timed fan delay allowing for drip time, set by means of the “Fnd”. In case of fault in the thermostat probe the start and stop of the compressor are timed through.
To print the manual completely, please, download it. Enter text from picture: Consider the maximum current which can be applied to each relay see Technical Data.
If the alarm LED is on, an alarm has taken place. Each LED function is described in the following table. Fit the probe where it is not accessible by the End User. Got it, continue to print.
electronic controller DIXELL XR60C | horecatiger
Push and immediately release the SET key: The instrument is provided with screw terminal block to connect cables with a cross section up nPS Pressure switch number: An additional parameter “FSt” provides the setting of temperature, detected by the evaporator. The instrument shall not be used for purposes different from those described hereunder. The fan sixell mode is selected by means of the “FnC” parameter:.
At the end of defrost dripping time is started, its length is set in the FSt parameter. Push and immediately release the SET key or wait for 5 seconds to. To see the kind of alarm, the max min. The instrument is fully configurable. Dixell Srl reserves the right to change the composition of its products, even without notice. Two defrost modes are available through the “tdF” parameter: Add to my manuals Add.